To day, I’ll show you video Goodman Heat Pump with HORRIBLE Duct System & How I FIXED It!!
The customer recently bought this home with new Goodman heat pump split unit HVAC equipment and they were experiencing high humidity levels on the second floor. They called out another company and the tech added refrigerant hoping that would fix the issue. After realizing that didn’t work, they called me out for a second opinion. First thing I did was hook up all my @Fieldpiece Products wireless probes with the @measureQuick app to get a full system diagnosis. I found the system running with little to no superheat and a low temperature drop (checking temps at the grilles in the space). I then hopped in the attic to inspect the air handler and duct system. Found the problem!! This duct system was hanging on by a thread. No screws, hardly any tape, several major gaps, etc! This unit was pulling in a lot of attic air! It is time for a little overhaul on this duct system. In this video I show my process on repairing the ductwork and removing refrigerant to get the system running right, hope you enjoy. LET’S DO SOME WORK!!
–SUPPORT THE CHANNEL–
(Use Promo Code “QUALITYHVAC” to save 10%!)
–TOOLS THAT I USE–
Veto ProPac LC Tool Bag:
Fieldpiece Job Link HVACR Charge & Air Kit:
Fieldpiece Job Link Pressure Probe:
Fieldpiece SC460 Meter:
Milwaukee PackOut Tool Box:
Milwaukee 12v Impact Driver:
Milwaukee Rechargeable LED Magnetic Light:
Appion 1/2″ Hose:
Appion 3/8″ Hose:
Appion Core Removal Tool:
Sporlan 3/8″ Flare Filter Drier:
Malco Sheet Metal Snips (Left Cut):
Malco Sheet Metal Snips (Right Cut):
Malco Sheet Metal Hole Cutter:
Malco Turbo Shear Cutter:
Malco Flex Duct Cutter:
Malco Panduit Gun:
–OTHER CHANNELS TO CHECK OUT–
#hvac #ductwork #hvachack
Thank for watching Goodman Heat Pump with HORRIBLE Duct System & How I FIXED It!!
Video Goodman Heat Pump with HORRIBLE Duct System & How I FIXED It!! with 9:22 length
See more at here!
Goodman Heat Pump with HORRIBLE Duct System & How I FIXED It!! uploaded in 2020-09-26 13:00:07 by Quality HVACR